Before attempting to install the Honeywell IGSMV4G Dual path communicator into your Vista 21IP hardwired system please make sure to power down the system including your backup battery and your transformer. Once this has been completed make sure that you have watched our previous video which will show you how to move the jumper on your 21IP system to the proper position in order to allow for external communicators. The first thing your going to want to do is run the 22 gauge by 4 wire through the back of the panel and begin wiring up the panel first. Take the black wire which will be the ground wire and make sure that goes into terminal 4. The second wire will be the power wire which of course is red place this in terminal 5. The yellow wire will go to terminal 7 and green will go to terminal 6 these two are your data in and data out terminals. Now that these are in place lets take the opposite side of the 22 gauge by 4 wire and begin to wire up the IGSMV4G dual path communicator.
Continuing on lets start by wiring in the ground or the black wire which will go into terminal 4. Next will be the red wire or “power” which will go into terminal 3. Terminal 5 you will want to wire in the yellow wire and lastly 6 will be your green wire again both of these are data in and data out. With this being wired up now you are ready to plug in your K14138LF wire which is what connects the communicator to the backup battery. Just a fun fact terminal one and two are for you ac transformer if you decide to wire in that way. Also, keep in mind you should always follow along with your instructions while working with your alarm panel.
For the lowest No-Term alarm monitoring rates contact GEOARM Security.
Alarm Monitoring for new or existing systems : http://www.geoarm.com/alarm-monitoring-services.html